Voltage Relationships Based on Voltage Ranges in ANSI C84.1-2016
110.16 Flash Protection.110.8 Working On or Near Electrical Conductors or Circuit Parts.(B) Shock Protection Boundaries. (C) Approach to Exposed Live Parts Operating at 5
Average Number of Thunderstorm Days in the USA Per Year Map
AC Equipment Ground (ACEG)Arrester Building Structural Steel (BSS) Electro-Static Discharge Protection (ESD) An Exothermic connection is a process for making a weld...
Earth Plus Conductive Concrete is Safety Protection Grid Solution is brand name for conductive concrete. Our Earth Plus Conductive Concrete has a resistance value around 20 Ohms per centimeter (cm).
The Information Technology Industry Council (I.T.I, formerly known as the Computer Business Manufacturers' Association, or CBEMA) provides a guideline that is a realistic, at-the-equipment, maximum allowable voltage that equipment can withstand witho
AC Service Entrance Disconnect Panel Station Ground Antennas (Roof Mounted) Antennas (Tower Mounted) Artificial or Chemical Ground Electrode System Coaxial Cables (Towers
List of Grounding Questions and Answers
Murphy's Law states, "If anything can go wrong, it will"
NEC adopted for each state May 2017
Duck Test The duck test is a humorous term for a form of inductive reasoning. It is explained this way: ”If it looks like a duck, swims like a duck and quacks like
Bonding and grounding maximizes personnel safety, equipment protection, and reduces noise that can be caused by powwer disturbances, RFI and EMI
The only purpose of a ground rod or a ground field is to have a designed electrical path for a static discharge voltage (such as lightning) to earth
NEC 90.1 states: The purpose of this Code is the practical safeguarding of persons and property from hazards arising from the use of electricity.
5 Step Solution to Elminate Equipment Damage
The real danger from electricity is an electrical shock. Dangerous electrical conditions are called risks and shock hazards
Why would any building or home need any surge protective device (SPD)?
External Building Earth Ground SystemHalo Ground System (HGS) usually consists of a #2 AWG minimum, non-insulated, solid or stranded wire routed around the inside perimet
We found all of these statements on the internet and thought that they were very interesting. All statements we have listed the person making the statement whenever possi